1 Jan Buy API 14FZ: RECOMMENDED PRACTICE FOR DESIGN, INSTALLATION, AND MAINTENANCE OF ELECTRICAL SYSTEMS FOR. 7 фев API RP 14FZ Recommended Practice for Design and Installation of Electrical Systems for Fixed and Floating Offshore Petroleum. Note: The protection techniques listed in API RP 14F and 14FZ are listed below for Divisions and Zones. Class/Division system. Intrinsically Safe Systems.
|Published (Last):||7 September 2011|
|PDF File Size:||12.78 Mb|
|ePub File Size:||17.97 Mb|
|Price:||Free* [*Free Regsitration Required]|
Therefore, temperature ratings have been produced to ensure that any gas release will not come into contact with a hot surface that could be near an autoignition temperature AIT.
Therefore, an accumulation of an explosive atmosphere could develop inside the enclosure. Resistant to mechanical abuse.
This table refers to the maximum skin temperature of the equipment. Published by Nickolas Allan Jenkins Modified about 1 month ago. Providing protection from fire, smoke, water and blast pressures. Zone 2 Equipment must be certified as meeting the requirements of the area this could be a number of different protection concepts.
Thus, the protection techniques for equipment to be installed in Zone 1 locations can be less demanding than the protection techniques for equipment to be installed in Division 1 locations.
Individual companies may and do install higher specification equipment and accessories above the levels stated during this course. A – Non-sparking equipment. Type ITC instrumentation tray cable Jacketed cable: If you wish to download it, please recommend it to your friends in any social system. Explosion proof equipment may not provide protection against the ingress of liquids or solids therefore, breathers and drains may be required.
We think you have liked this presentation. Electrical equipment suitable for Zone 1 locations is not required to be suitable for locations where flammable gases and vapors may be present continuously or for long periods of time, i. The motor design and construction should be suitable for both the load application and environmental conditions. Inch, size or larger conduit run entering an enclosure that contains splices, taps, or terminals. The correct type of threads shall be installed or listed or labeled threaded adaptors suitable for the location.
Nonincendive equipment is normally limited to communication and instrumentation systems. All seals should be installed as close as practicable, but in no case more than 18 inches, from the enclosures to which they are attached. Mineral-insulated metal-sheathed cable as defined by NEC Article You are permitted to work on an I.
WELCOME LEARNERS! UpStream (API RP 14FZ, API and API ) – ppt download
Forside Nettbutikk Produktkatalogen Produktpresentasjon. This ensures that the gas or vapor located above the arcing or sparking parts or the gas or vapor located exterior to the enclosure cannot be ignited by the electrical arcing parts within the oil.
What is Nonincendive equipment? As tested by the NFPA Same as shipboard cable, marine. They accomplish this by maintaining a r; seal.
With nonincendive equipment make-and-break contact need not be explosion proofoil immersed or hermetically sealed. Therefore, process and operational temperature must be considered to correctly classify hazardous areas and calculate the temperature ratings.
These advantages may include reduced initial capital expenditures, enhanced safety, or facilities that are more easily and more economically maintained.
WELCOME LEARNERS! UpStream 500 505 (API RP 14FZ, API 500 and API 505)
This may result 1fz more cost effective installations or equipment that is more easily maintained. Metal-clad cable for hazardous locations as defined in UL MI cable: The guidelines presented herein should 1fz a high level of electrical safety when used in conjunction with well-defined area classifications. This document recommends minimum requirements and guidelines for the design and installation of new piping systems on production platforms located offshore.
Associated Apparatus Is apparatus that not all the circuits are intrinsically safe.
ali Strict rules must be followed, system calculated to ensure energy levels are within tolerances and diagrams must be followed closely as wells as the current RP, Codes and Standards. They should always be installed in the unclassified area or be provided with an alternative means of protectionpurged or mounted inside and explosion proof box. This course covers the minimum requirements for installations within hazardous areas.
This document provides guidelines and recommended practice for the satisfactory design of offshore structures against fire and blast loading. Only suitable for Division 2 and unclassified locations.